TYPE - NM A general purpose, nonmetallic liquidtight conduit offers excellent protection to wiring from abrasion, sunlight, mild acids, alkaline and oils. Often used for air conditioning hook-ups and other outdoor applications.
CONSTRUCTION: Type NM is a helically wound integral Type B construction. It contains a spiral of rigid PVC reinforcement imbedded within the PVC wall.
APPLICATION: Type NM is intended for installation in accordance with Article 356 of the NEC (ANSI/NFPA-70) for Flexible Liquidtight Nonmetallic Conduit (LFNC-B or FNMC-B). -For containment of 1000 volt and lower potential circuits. -Listed and marked for outdoor use. -Listed and marked for direct burial and in poured concrete -Installations in hazardous (classified) locations: Class I Div. 2 Article 501 Class II Div. 1 & 2 Article 502 Class III Div. 1 & 2 Article 503 -Electric signs and outdoor lighting over 1000 volts.
Article 600.32(A). -Wiring methods for pools and spas. Article 680. -Conforms to the requirements of section 14.5.5 of the Electrical Standard for Industrial Machinery NFPA-79.
Listed File # E79308 Conforms to Underwriters Laboratories Standard ANSI/UL 1660 Type B.
Certified File #LL230485 Conforms to CSA 22.2 No. 227.2 Type B.
Fittings: Suitable for use with nonmetallic fittings marked for FNMC-B or LFNC-B for liquidtight flexible nonmetallic conduit Type B or with standard metal liquidtight fittings. See NMLT connectors for further information.